- Fire pump controller enclosure shall be standard NEMA type 2 (IP 31) drip
proof suitable for wall mounting. The enclosure shall have a bottom entry
gland plate. It will be provided with a key lock handle. It will be painted red
RAL 3002 as per NFPA 20.
- The controller will have a fused horsepower rated door interlocked rotary
type disconnect switch. This switch shall be capable of being padlocked in the “OFF” position during installation or maintenance.